Published on November 7, 2007
DOE/Sandia National Laboratories Coordinated Approach for LNG Safety and Security Research: DOE/Sandia National Laboratories Coordinated Approach for LNG Safety and Security Research Briefing to NARUC Staff Subcommittee on Gas July 15, 2007 Tom Blanchat, Anay Luketa-Hanlin, Mike Hightower, Sheldon Tieszen Fire Science & Technology, Energy Systems Analysis Sandia National Laboratories James Slutz, Deputy Assistant Secretary, Office of Petroleum and Natural Gas Christopher J. Freitas, Program Manger, Natural Gas Storage, Pipeline Reliability, and LNG, Office of Oil and Natural Gas United States Department of Energy Key Features of LNG Spills Over Water: Key Features of LNG Spills Over Water Hole Size/ Spilled Volume Liquid Vaporization Liquid Spread Fire Increases Vaporization Thermal Damage Due to Fire Wind Tilts Fire Fire Entrains Air Waves Affect Liquid Spread If Ignition Occurs Analysis Requires Adequate Representation of Key Features Cryogenic Damage from LNG Spill Artist’s Rendering Not to Scale Other possible hazards Confined space explosion Late ignition and vapor cloud fire GAO-07-316 Maritime Security - Public Safety Consequences of a Terrorist Attack on a Tanker Carrying Liquefied Natural Gas Need ClarificationFebruary 2007Conclusions: GAO-07-316 Maritime Security - Public Safety Consequences of a Terrorist Attack on a Tanker Carrying Liquefied Natural Gas Need Clarification February 2007 Conclusions “…Understanding and resolving the uncertainties surrounding LNG spills is critical, especially in deciding on where to locate LNG facilities…. …Additional research to resolve some key areas of uncertainty could benefit federal agencies responsible for making informed decisions when approving LNG terminals and protecting existing terminals and tankers, as well as providing reliable information to citizens concerned about public safety.” GAO-07-316 Maritime Security - Public Safety Consequences of a Terrorist Attack on a Tanker Carrying Liquefied Natural Gas Need Clarification February 2007 Recommendation for Executive Action: GAO-07-316 Maritime Security - Public Safety Consequences of a Terrorist Attack on a Tanker Carrying Liquefied Natural Gas Need Clarification February 2007 Recommendation for Executive Action “To provide the most comprehensive and accurate information for assessing the public safety risks posed by tankers transiting to proposed LNG facilities, we recommend that the Secretary of Energy ensure that DOE incorporates the key issues identified by the expert panel into its current LNG study. We particularly recommend that DOE examine the potential for cascading failure of LNG tanks in order to understand the damage to the hull that could be caused by exposure to extreme cold or heat.” Expert Panel’s Ranking of Need for Research on LNG Experts Suggest Future Research Priorities to Determine the Public Safety Impact of an LNG Spill: Expert Panel’s Ranking of Need for Research on LNG Experts Suggest Future Research Priorities to Determine the Public Safety Impact of an LNG Spill Rank Research area In Progress / Proposed Large fire phenomena √ Cascading failure √ Large-scale spill testing on water √ Large-scale fire testing √ Comprehensive modeling: interaction of physical processes √ Risk tolerability assessments √ Vulnerability of containment systems (hole size) √ Mitigation techniques √ Effect of sea water coming in as LNG flows out Impact of wind, weather, and waves Source: GAO Sandia LNG Activities: Sandia LNG Activities December 2004, DOE “Guidance on Risk Analysis and Safety Implications of a Large Liquefied Natural Gas (LNG) Spill over Water”, SAND2004-6258 Classified Vulnerability Analysis & Breach Research USCG Cabrillo Deepwater Port (California), January 2006, US Coast Guard “Review of the Independent Risk Assessment of the Proposed Cabrillo Liquefied Natural Gas Deepwater Port Project”, SAND2005-7739 New England Deepwater Ports (Massachusetts) April 2006, US Coast Guard “Independent Risk Assessment for Neptune and Northeast Gateway Deepwater Ports”, report by Acutech Consulting Group for USCG Calypso Deepwater Ports (Florida) Others in progress Large Scale Spill and Fire Research Proposed Cascading Failure Research LNG Spill Safety Analysis andRisk Management GuidanceSAND2004-6258: LNG Spill Safety Analysis and Risk Management Guidance SAND2004-6258 Provide direction on hazards analysis Identify “scale” of hazards from intentional events Provide direction on use of risk management to improve public safety Provide process for site-specific evaluations Study used many resources: experts from academia, government and industry on LNG vessel design and operations, explosion and fire modeling, terrorism, and risk management Structural Analysis Approach for Attack and Breach of LNG Ship: Structural Analysis Approach for Attack and Breach of LNG Ship Detailed 3-D ship calculations using the shock physics code, CTH, developed at Sandia Multi-dimensional, multi-material shock wave propagation and material motion. Structure modeled using finite elements - billions of nodes required to resolve thin-walled structures Using massively parallel computers, 1000 - 3000 processors Full scale, detailed model geometry Water, LNG, and thermal insulation on tank included Assessing different explosive charge shapes, sizes, and standoff distance from hull Slide9: Sample 3-D Calculation Result View of inner hull damage Thin structures are resolved using adaptive mesh refinement Lower portion damaged from impact of water thrown inward from blast Upper portion damaged from thrown fragments from outer hull (1 ms = 1/1000 second) A Coordinated Plan for LNG Safety and Security Research: A Coordinated Plan for LNG Safety and Security Research LNG Fire Physics – In progress Objective: To determine if calculated thermal hazard distances can be reduced from conservative estimates by an order of magnitude for large-scale LNG pool fires. Cascading Failure - Proposed Objective: Determine if intentional attacks could result in cryogenic or fire-induced damage to the ship structure that would lead to cascading (multi-tank) structural failures and catastrophic release of LNG. Develop an expected timeline for cargo release based on the postulated scenarios Mitigation - Proposed Objective: Develop mitigation options to reduce the risk to ships at land-based and deep water ports. Where appropriate, provide benchmark test data and analyses required to plan mitigation strategies. LNG Fire Physics Research: LNG Fire Physics Research Reduced-scale Tests in SNL’s Thermal Test Complex (TTC) – In Progress Objective: Determine the flame height as a function of pool diameter and the critical diameter for mass fire behavior to obtain best estimates of fire surface area Large-scale LNG pool fire tests - In Progress Objective: To determine trends in flame height, smoke production, and burn rate CFD model development for LNG pool fires - Proposed Objective: To use CFD and analysis to predict fire behavior at the scales of interest and to provide guidance to industry. Small Scale LNG Pool Fire TestsQ* correlation for flame height & mass fire: Small Scale LNG Pool Fire Tests Q* correlation for flame height & mass fire Flame height for LNG pool fires (~100 m) is uncertain. Mass fire behavior is also unknown. Previous studies have not used burners which result in fully turbulent fires (i.e. different physics). Controlled fuel flow rate experiments. develop flame height correlation investigate mass fire behavior Will compare correlation to measured flame heights from large scale tests. Thermal Test Complex at Sandia, 3 m diameter gas burner capability 3-m diameter hydrogen test observed by the DOE/NARUC LNG Partnership on 3/21/2007 Flame Coherence vs. Mass Fire: Flame Coherence vs. Mass Fire Height/diameter (L/D) ratio is between 1.0 and 2.0 based on current flame height correlations for pool diameters 200 – 500 m Large fires (D>100 m) generally break up into ‘mass fires’, characterized by a low L/D ratio (< 0.5) e.g. forest fires Presently unknown at what diameter very large LNG fires will exhibit mass fire Use Q* correlation to predict mass fire Very different thermal radiation view factors Mass fire Rcoherent RMass Fire Thermal hazard distance will be reduced with lower flame height Coherent Thermal hazard distance: 5 kW/m2 heat flux is the commonly used value for establishing fire protection distances for people (30 second exposure causes 2nd degree skin burns (blisters) at this distance) DOE/SNL Large Scale LNG Spill Fire ExperimentsPurpose, Approach, and Anticipated Benefit: DOE/SNL Large Scale LNG Spill Fire Experiments Purpose, Approach, and Anticipated Benefit Anticipate a significant increase in Liquefied Natural Gas (LNG) tanker deliveries to U.S. ports Public safety concerns from an accidental or intentional spills have increased While improvements have been made over the past decade in assessing hazards from LNG spills, the existing experimental data is much smaller in size and scale than many postulated large accidental and intentional spills Large scale experimental data is needed to develop and validate fire models to address current spill and hazard assessment deficiencies DOE and SNL will perform LNG spill fire experiments (on water) at intermediate to large scale (~40 m up to 100 m diameters) Experiments will generate knowledge on fire parameters such as smoke generation and shielding, flame height, thermal flux, and burn rate as a function of pool size Potential to significantly reduce hazard distances from an LNG spill over water Smoke Shielding: Smoke Shielding No smoke shielding at 10 m scale LNG (100% methane) spill and pool fire on water 300 gpm spill rate 10 m diameter fire SNL Water Impact Facility Fact: Emissive power decreases with increasing fire size due to smoke shielding Smoke Shielding: Smoke Shielding The smoke shielding is expected to increase for large LNG fires, however, the amount of smoke shielding is unknown. JP8 – 2 m (SNL) JP8 – 3 m (SNL) JP8 – 20 m (China Lake) LNG – 20 m Maplin Sands Tests – 1982 LNG – 35 m Montoir Tests – 1989 LNG ~ 200 m ????? DOE/SNL Large LNG Fire ExperimentTest Methodology: DOE/SNL Large LNG Fire Experiment Test Methodology Identify reservoir design criteria and appropriate test site SNL/NM D Explosive Test Site 900 m diameter hazard zone fully within Sandia property Construct a 120 m diameter water pool (1 m deep) Construct a reservoir to contain up to 310,000 gallons LNG Construct reservoir systems and channel to discharge LNG at pool center Construct LNG process fill piping Install reservoir, pool, and perimeter instrumentation (flow rate, meteorology, video, IR, heat flux, etc.) Conduct minimum 3 baseline tests Design criteria: 1) Mass flux = 0.2 kg/m2s (yielding a burn rate of 5 x 10-4 m/s), 2) Spread time = 3 minutes (for the 100 m diameter pool), and 3) Steady-state pool fire duration = 2 minutes. Determines a reservoir liquid capacity of 310,000 gallon (1175 m3) Large LNG Experiment Description: Large LNG Experiment Description LNG gravity released onto a 120-m diameter water pool (1-m deep). Concrete-lined soil-bermed reservoir supplies pipes that extend from the reservoir bottom to a covered collector box. LNG flows on an open concrete channel to the center of the pool. Capped reservoir vents LNG vapors during the filling process. Large diked impoundment area in event of reservoir leakage Cascading Failure of LNG ShipsProposed Research: Cascading Failure of LNG Ships Proposed Research Objectives: Determine if intentional attacks could result in cryogenic or fire-induced damage to the ship structure that would lead to cascading (multi-tank) structural failures and catastrophic release of LNG. Develop an expected timeline for cargo release based on the postulated scenarios Cascading Failure Due toCryogenic DamageProposed Research: Cascading Failure Due to Cryogenic Damage Proposed Research Approach: Perform scaled tests on a prototypical model that has some of the typical structural features found in an LNG ship, by exposing portions of the prototype model to Liquid Nitrogen (LN). Test data used to confirm that computer simulations are realistic and adequately represent the physical event. Full-scale LNG vessels would be analyzed with specified structural degradation in locations where cryogenic damage may occur. 30-40 m3 LNG spill on deck results in brittle fracture Source: A. Valudolon (2000) Cascading Failure Due to FireProposed Research: Cascading Failure Due to Fire Proposed Research A large spill is likely to result in a large fire that would partially engulf the ship. Thermally induced structural failure is likely if the temperature of the structural steel of the vessel reaches a critical value. A flux and temperature profile will be calculated based on the cargo discharge timeline. These initial conditions will be passed to a simulation capable of predicting ship response with blast and thermal damage. MitigationProposed Research: Mitigation Proposed Research Objective: Develop mitigation options to reduce the risk to ships at land-based and deep water ports. Where appropriate, provide benchmark test data and analyses required to plan mitigation strategies. Mitigation strategies: Prevent an LNG tank breach (security measures to thwart an attack are included in this category). Reduce the severity of the spill. Reduce fire hazards. Structural Breach and Fire MitigationProposed Research : Structural Breach and Fire Mitigation Proposed Research The protection of LNG Carriers and Deepwater ports, as well as land-based facilities, should be based on a defense-in-depth strategy. In the event that active protection and structural mitigation strategies fail, it is important to develop improved methods to reduce the hazards from a pool fire. Structural: Matrix of benchmark tests and analyses to identify vulnerabilities. Utilize benchmark tests to validate modeling and simulation used for damage predictions. Structural damage from a boat attack Structural (cryogenic) damage from small standoff devices leading to cascading failure event Insider/on-board attack Develop mitigation strategies and recommendations to harden the ship to attack. Fire: Possible methods that could be investigated include: Adding heavier hydrocarbons which would increase smoke shielding. Strategically adding foam to help quench the fire. Heat flux smoke curtains. Looking to the Future: Looking to the Future CFD model development for large-scale LNG pool fires Pool regression rate model for Heat Release Rate Validated soot model for Heat Flux Simulation for design of a weapons test using FUEGO The design of the qualification experiment in the new cross-wind test facility with Fuego represents the accreditation test of our modeling and simulation capability by the weapons community.